In the early 20th century, a bell signalling system was used Underground in the coal mines. The bell was connected by two unprotected wires to a Leclanché cell (battery), In order to signal down the tunnel the miner would short the wires with his spade, completing the circuit and ringing the bell.
In the aftermath of a major explosion at the Senghenydd Colliery (Wales) in 1913, caused by the signalling system, it was realised that by reducing the size of the Leclanché cell i.e. reducing the voltage and current capability, sparking no longer occurred.
The applications for this were limited to low power battery systems until the development of semiconductors in the 1960s when the concept of intrinsic safety was developed based on removing the ignition source by reducing the power in the circuit to keeping heating below ignition levels and completing remove any chance of sparking
Ex i EN 60079-11 Explosive atmospheres. Equipment protection by intrinsic safety "i"
Unlike all other protection methods intrinsic safety is the system concept, not just an individual entity but a combination of interconnected entities.
Assuming a device is not self-contained i.e. portable then there will be at least two items (plus cable) to form a circuit knowns as a loop.
Each item in the loop can be one of 4 types:
Associated Apparatus is generally thought of as a stand-alone zone barrier or isolation interface (known colloquially as the barrier) but it applies to any equipment with intrinsic safety and non-intrinsic safety terminals as the barrier may be built in to other equipment e.g. distributed I/O cards or output from an alternatively protected Hazardous area device such as a thermocouple connected to an Ex d transmitter.
The Associated apparatus limits the power, voltage and current, out to the hazardous area and field equipment and does not allow for installation in the hazardous area unless another protection method (listed in EN 60079‑0) is also used
Simple apparatus does not need to be certified and consequently does not require a certification label. However, it may require to be identified with a label so it can be easily recognised as simple apparatus rather than uncertified equipment in the hazardous area.
Equipment which has an approved body type certificate (Intrinsic Safety) for Atex Category 1 & 2 or for Category 3 a competent person’s certificate e.g. by the manufacturer or other certification body.
Cables are not simple apparatus and do not require to be certified.
Intrinsic safety has a very low physical requirement for the construction and protection of cables compared with all other protection methods. The minimum is a double insulation i.e. multiple cores and outer sheath. Armour or protective sheath is not required although may be required to comply with site standards or other local site conditions to ensure segregation from non-intrinsically safe circuits.
Single cores cables are not allowed unless they are otherwise protected i.e. internally to an enclosure.
As Intrinsic Safety is a system Concept the complete loop must be documented in the form of a Descriptive System Document
Occasionally intrinsic safety is used completely internally on equipment to go into the hazardous area. The most common use is on sparking (switches) or inductive components switches to obtain a non-sparking apparatus certificate. In this case there will be no external intrinsic safety connections and it will be evident only from the equipment certification and label e.g. II 3G Ex ic nA IIC T4 Gc
Of course, Intrinsic Safety can also be used for portable equipment, the same principles apply but all part are contained in a single enclosure and the power limited within the battery assembly. As the power comes from internal source i.e. battery, the voltage is limited by definition and the current available will be limited by a resistor or, depending on battery type and size, internal battery resistance.
If limited by an external resistor this generally should be built in the form of a failsafe assembly and encapsulation is often used. For items using small batteries such as watches and hearing aids, the batteries inherent internal resistance may be sufficient.
Although the primary protection for dust is by enclosure Intrinsic safety is a very good method of protection as it is based on energy within the circuit and as previously shown the energy allowed for dusts is generally orders of magnitude higher gas, although care must be taken with creepage and clearances when using conductive dusts.